Find great deals for Fireye Eb E Flame Monitor Chassis and Cover EB Shop with confidence on eBay!. At Apex Controls you will find the EB along with other HVAC/R item(s) you need at the most competitive prices in the industry. Fireye EB – EB Flame-Monitor Control Replacement Chassis – The Flame -Monitor Series provides the proper burner sequencing.
|Published (Last):||11 October 2007|
|PDF File Size:||9.21 Mb|
|ePub File Size:||2.18 Mb|
|Price:||Free* [*Free Regsitration Required]|
Burner programmers have entered the computer age with microprocessor technology. The technology is enhancing their capabilities at an accelerated rate.
The Series was a completely new line, from the wiring base up. Nothing in the Series was compatible with previous Honeywell programmers, as far as wiring was concerned. Even terminal designations were changed. The E Series from Fireye, with ED display module, catches up to the concept of the Series, fireyee no wiring changes from the E In order to complete the entire programmer, a wiring base, for surface mounting, or a for panel mounting, eb7700 EP programmer module, and a flame amplifier module was needed.
No display module was included!
A display module must be added to the E! The major difference between the E and the E was that the E came with a display module ED and the E did not.
Fireye EB chassis – In Stock
The E mounting screw was shorter than the mounting screw with the E The E plus a display module was priced exactly the same as the old E; therefore, Climatic Control Company will stock only the E from now on.
What really differentiated the latest version of the Flame-Monitor from its predecessor are the enhanced EP programmer and the ED display. The improved EP programmers did not have new numbers to differentiate them from the old style EP programmers, since they were totally compatible figeye any Flame-Monitor. Any old E that requires an EP replacement can use the improved programmer. Fireye deliberately did not change the numbers of the EP programmers to emphasize this compatibility feature.
The new EP programmers come with six dipswitches to give the user various selectable functions, and the ability to use the new ED display. The user has the ability to use an ED display in place of an ED, but they do not have to replace an existing ED when replacing fireyf EP programmer. Using the new EP programmer, just as it comes out of the box, duplicates the function of the old EP being replaced.
Once the new-style programmer is in a Flame-Monitor, the ED display can be used. The ED display is priced exactly the same as an ED The ED is now an excellent service tool, similar to the Honeywell S The ED can access historical information and identify the components of the Flame-Monitor being used through use of a tactile three-key keypad. When plugging in the ED display, be sure it is powered down to prevent arcing of the cable pins that could damage the ED or programmer.
The ED could eliminate the need for an E service tool. The E service tool has much more capability than an ED, but the E is expensive. In most cases, the diagnostic information available through the ED is all a service technician needs to diagnose ifreye problems.
Fireye Flame-Monitor: New and Improved Technology
The programmers can overwhelm the E with a burst of information that the E cannot handle. Fireye is working with the manufacturer of the E to solve this problem, but as of this writing, has no solution.
First, there are no changes in the wiring bases or amplifiers. Second, remember the E is an E without a display. Third, the EP programmers have been enhanced, but their number designation remains the same to emphasize their backwards compatibility. The features added to the EP programmers are a set of six dipswitches.
On the EP,, and For eb7000, if the A. After one minute, if 3 to P remains a closed circuit, the control will lock out. On the EP, andall 6 dipswitches are active: Determines if the control will recycle or not recycle on detecting an open circuit between 3 and P.
Configures terminal 6 rireye be either intermittent or interrupted ignition. It is a complete redesign of the ED It mounts directly to the front of the new style EP programmers and accesses the programmers with a short plug-in cable included with every ED The ED can be remotely mounted by using or mounting kit. These kits consist of a mounting plate, eg700, two mounting screws, and a connecting plug-in cable, 4′ long in the8′ long in the kit.
An ED is similar to the ED, but uses telephone jack connections instead of cables. Remote reset only, still uses the ED cables. Remember, remote operation of fb700 ED is also requiring the reset to be remote too, eb7700 reset is built into the ED Fireye is very aware of this problem.
Once thawed out, it is supposed to function again. With the new EP programmer, power supply at reasonable cost was at a premium.
Fireye Eb-700 E110 Flame Monitor Chassis and Cover EB700
A change may be made. Be sure to refer to the latest bulletins for up-to-date information, as these bulletins are no longer current. Bulletin ED, page 2, contrast control. The contrast control is not designated in any way. It is the recessed allen-head screw in the back of the ED If the ED is used as a service tool or in a remote area, it needs a back to cover the printed circuitry. For now, a homemade back can be made of any non-conducting material.
Fireye will soon have a thin piece of plastic for this. Bulletin E shows no ambient limits for the E This is actually an E They actually are available in 6, 15, and 25 feet lengths, as their number indicates after the dash.
This is true only if using the ED cables. The E will work with the new EP programmers fb700 code 28 when using the telephone jack system. Instructions are supposed to be coming in the reprint of E and ED This should not be there. There is no H.
Fireye Type EB See E or E Bulletin Flame Monitor – no box. | eBay
Bulletin EP, Aprilpage There is nothing in Bulletin E about this. You need a disc, E or E software, and an instruction sheet. New and Improved Technology. December 9, – 2: Testing Wireless Solutions Testing wireless transmitters link. Product Code Quantity 1 2 3 4 5. Request Our Free Catalog.